Condition Monitoring of Power Transformers
One major issue with the SFRA measurements is their repeatability on-site in the range of high frequencies when it comes to periodic condition monitoring of transformer windings. SFRA measurements can be affected by a number of factors such as layout and grounding resistance of the ground extensions of SFRA cables which may lead to misinterpretation of the test results.
Dr Andrey A. Reykherdt, Senior Condition Monitoring Engineer, Select SolutionsRead More
Fault Investigation on Power Transformers
Fault investigation on a 150 MVA 220/66/10.9 kV power transformer performed by Select Solutions in collaboration with AusNet Services utilising a great experience of condition monitoring engineers and asset management in finding a root cause of an electrical fault in the transformer.
By Andrey Reykherdt, Don Taylor, Junming Kuang, Mark Cotton, Adam Suleiman, Christopher Cox, Tim Pasanduka - AusNet Services* Select Solutions, A Division of AusNet ServicesRead More